9.1.1 Electrical service is nominally 240 or 480 V at the transformer power supply. ... The starter control circuit shall be wired with three-wire control. ... Conductors of motor control circuits shall be protected against overcurrent in accordance with their ampacities as ... When used, magnetic oilers shall be wired from the motor terminals (see figures 8 and 9; also see Rule 14-100, Canadian Electrical Code).
|Title||:||ASAE standards 2000|
|Author||:||American Society of Agricultural Engineers|
|Publisher||:||Inside New York - 2000-08|