8-11 TOTAL HEAT GAINS To obtain the total cooling equipment load, multiply the total sensible heat gain by 1.3. ... room is determined in the following manner: A. Obtain the sum of the calculated heat gains of all rooms to be conditioned (total of Line 20, Worksheet J-1). B. Obtain Capacity Multiplier from Table 7 corresponding to the outside design conditions and the desired inside temperature swing.

Title | : | Environmental Systems Library: [manual]. |

Author | : | Air Conditioning Contractors of America |

Publisher | : | - 1955 |

Continue