Thermodynamic Design Data for Heat Pump Systems provides a comprehensive data base for the design of vapor compression heat pump systems, particularly in industrial applications where careful matching is essential. The book contains two chapters and 21 appendices. Chapter 1 describes how the data in the graphs and tables in the appendices have been derived, and chapter 2 gives examples of how the data can be used. The appendices present the required design data for 21 materials which are likely to be used as heat pump working fluids.A Comprehensive Data Base and Design Manual F. A. Holland, F. A. Watson, S. Devotta ... The enthalpy of a#39;e twA³ phase mixture at D1 can then be calculated from the enthalpies of the saturated liquid H.2 and of the saturated ac D3 vapour HD2 from Equation (1.11) HD1 * aquot;D3 X + ... Rankine coefficient of performance (COP), against gross temperature lift (T O TE ) for heat pump systems operating on R12.
|Title||:||Thermodynamic Design Data for Heat Pump Systems|
|Author||:||F. A. Holland, F. A. Watson, S. Devotta|
|Publisher||:||Elsevier - 2013-10-22|